CP 1800QTL-ECX AV
Audio Visual Cooling Unit
*Shipments to AK and HI – Please call for a quote
CellarPro 1800QTL-ECX-AV Audio-Visual Cooling Unit (P/N 2180). CellarPro’s 1800QTL-ECX-AV cooling unit has been optimized to provide consistent, cool conditions for Audio-Visual equipment storage rooms.AV equipment often creates heat that must be managed in order to avoid damaging expensive electronic components. Our 1800QTL-ECX-AV audio-visual system uses energy-efficient EC fans and is designed to generate 1584 SENSIBLE BTUH and maintain 75F in conditioned environments below 40% RH. Please note: This unit is subject to a 5-20% BTUH correction factor above 40% relative humidity. Ambient relative humidities greater than 60% exceed the design limits of this cooling system.
1584 SENSIBLE BTUH @ 75F.
CellarPro 1800QTL-ECX-AV Audio-Visual Cooling Unit (P/N 2180). CellarPro’s 1800QTL-ECX-AV cooling unit has been optimized to provide consistent, cool conditions for Audio-Visual equipment storage rooms.
AV equipment often creates heat that must be managed in order to avoid damaging expensive electronic components. Our 1800QTL-ECX-AV audio-visual system uses energy-efficient EC fans and is designed to generate 1584 SENSIBLE BTUH and maintain 75F in conditioned environments below 40% RH. Please note: This unit is subject to a 5-20% BTUH correction factor above 40% relative humidity. Ambient relative humidities greater than 60% exceed the design limits of this cooling system.
Our cooling units are designed to be used in properly-constructed wine cellars that are adequately insulated, airtight and sealed with a vapor barrier. In improperly-constructed cellars, the cooling unit will create excess condensation, leading to damage and premature failure of your cooling unit (not covered by warranty).
- On the hot side, this unit intakes from the rear, and offers a choice of top or rear hot exhaust.
- On the cold side, this unit intakes from the front and exhausts from the bottom (thus the front 8 inches of the cooling unit must be inside the cellar.)
- The 1800QTL-ECX-AV requires fresh air intake at the rear of the cooling unit. If sufficient space does not exist to provide sufficient airflow to the rear of the cooling unit, you may need a rear duct kit.
- 1800 Series cooling units can be installed completely inside the wine cellar when used with our rear duct kit, which allows you to duct the supply and return airflows from the rear of the cooling unit up to 100 equivalent feet (50 feet per duct).
- Please note: The cold side of the 1800 Series cooling units cannot be ducted, and the hot side can be ducted with 6-inch ducting (no reductions) plus auxiliary fan support, which is included with our our rear duct kit.
- You must located this unit within the cellar, with the following exception: these units can be installed directly above the wine cellar when used with our front intake hood.
- For installation in environments below 40F, our compressor heater modification is required.
- For installation in environments below 20F down to -20F, we recommend our Fan-Cycling Switch (P/N 6972) combined with our compressor heater.
- A CellarPro cooling unit must always be used in the upright position, and should never be operated on its side or upside down.
Size: 18w x 16 1/2d x 10 1/2h (in)
Weight: 60 lbs
115V AC / 60 Hz
– Running: 2.4 Amps
– Startup: 14.2 Amps
– Total Watts: 191
– Requires: Dedicated 15-Amp Circuit
– Recommended: Surge Protector
Decibels: 41 dBA (Rear)
Capacity: 1584 BTUH @ 75F*
– Warranty Overview
Click on one of the following links for more information:
– Owner’s Manual
– Product Brochure
– Rear Drawings – As Ducted
– Mounting Clips
– Front, Rear & Side Views
– Top & Bottom View
CellarPro 1800QTL-ECX-AV Cooling Unit (P/N 2180). CellarPro’s 1800QTL-ECX-AV cooling unit is engineered to maintain ideal temperature conditions in Audio-Visual equipment rooms. 1800QTL-ECX-AV uses an optimized compressor and oversized coils to generate cool, consistent 75-degree temperatures with minimal noise.
All air-cooled refrigeration equipment requires fresh air intake to dissipate the heat generated by the cooling unit. The fresh air intake CANNOT come from the wine cellar space – it must come from space outside the cellar. Designed for indoor use only, 1800QTL-ECX-AV units can operate in environments ranging from 95F to 40F out of the box. To operate the unit in colder temperatures, please see modifications listed on the Options & Upgrades tab.
- Now with energy-efficient EC Fans on both the cold and hot sides, save $39.02 in annual energy costs vs AC fans (assumes 75% runtime and $0.15/kWh)
- This unit offers a choice of top or rear hot exhaust. If the unit’s location does not provide sufficient room for airflow, you may need to purchase a rear duct kit.
- Adjustable humidity control combines a high-output compressor with flexible fan cycles to maintain a recommended level of moisture inside your cellar.
- Extra-large coils generate maximum cooling power.
- Commercial-grade Electrofin coating protects the evaporator coils from leaks and corrosion.
- 100W Heating Element and 1/2-Inch ID Drain Line are included as standard equipment to burn off and channel excess condensation.
- Intuitive LED display panel mounted on the evaporator with digital programmable thermostat is simple and easy to use. Remote thermostat is available as an upgrade.
- Energy-saver mode, quick-chill mode, and auto-defrost cycle provide convenient solutions to common cellar needs.
- Temperature set point range is 60F to 78F when the cooling unit is properly sized.
- Unit operates with minimal vibrations and less noise than comparable units from competitors.
- Audible and visual alarms and maintenance-needed indicator protect the cooling unit and the wine cellar.
- 10-foot power cord exits from the rear and plugs into standard 110V receptacles.
- Common dedicated 15-amp circuit is required to power the unit.
- 3-amp electric receptacle is provided to run a small lamp.
- Removable steel case provides access to the internal components for servicing and repair.
- CellarPro’s 2-Year Standard Warranty, the most thorough in the industry, protects the unit against manufacturing defects.
- ETL Tested and Certified to rigorous UL Standards for safety.
- Compressor Heater #1727: protects the unit when installed in environments that drop below 40F down to 20F.
- Fan Cycling witch #6972: supports the unit in temperatures below 20F and as low as -20F when combined with our compressor heater.
- Duct Intake Hood (Cold Side) #1932: permits the cooling unit to be placed directly above the cellar.
- Duct Hood (Hot Side) #7409: allows you to install the unit completely inside your cellar or in a small space with limited airflow. Includes an auxiliary fan, but no ducting.
- Duct Kit (Hot Side) #1439: same as the Duct Hood, this kit also includes 2 x 25-feet of 6-inch insulated (R-6) flex ducting.
Filters & Grills
- Use our filter & grill guide to find the cooling unit filter or duct filter and/or duct grill that is appropriate for your cooling unit.
Remote Control & Probe
- Remote Display #1603: lets you place the digital panel wherever you want, whether inside or outside the cellar. Includes 10 feet of wiring.
- Bottle Probe #1434: this remote thermostat with a 10-foot cord overrides the thermostat on the face of the cooling unit, and allows it to monitor air or liquid temperatures at various locations inside the cellar.
- Extension cords available in 25-foot (#1780) and 50-foot (#1781) lengths.
Other Options & Upgrades
- Rear Condensate Drain Line plus Heating Element are included as standard equipment.
- Power Cord Modification #1098: normally the cord exits from the rear of the cooling unit, which generally is outside the cellar; this modification moves the cord to the front of the cooling unit, so that it can be plugged into an outlet inside the cellar.
- Mounting Clips #1095: attached to the front of CellarPro 1800 Series cooling units, these clips are designed to be bolted to the ceiling inside the wine cabinet / cellar.
DID YOU KNOW?
Nobody protects your wine cellar better than CellarPro Cooling Systems! In the event your cooling unit fails and the failed components are covered by our warranty, we’ll send a replacement cooling unit to you per the terms of our Replacement Unit Program
CellarPro Replacement Unit Program
If your CellarPro cooling unit fails and the parts that failed are still covered by warranty, we’ll send a replacement cooling unit to you, as follows:
- Your cooling unit must be registered at CellarPro
- Your cooling unit must have been properly sized, installed and maintained
- Your cooling unit may not have been permanently modified, damaged or disfigured
- Replacement units are factory-refurbished cooling units with a similar build date as your original unit
- You are responsible for the shipping cost to send the replacement unit to you and return the original unit to us, and the cost (if any) to remove the original unit and install the replacement unit
- In order to send a replacement unit, we require a deposit, which will be refunded minus shipping costs upon the return and pending the inspection of the original unit
- If the original unit failed due to improper intallation or use, the failure is not covered by warranty and we will deduct the cost of the repairs from the refund of your deposit